|Product Name:||H05VVH6-F 4 Core Copper Flat PVC Insulated Cable||Conductor:||Copper|
|Insulation Material:||PVC||Operating Temperature:||-40℃-+70℃|
|Jacket:||PVC||Standard:||BS EN 50214|
H05VVH6-F PVC Insulated Cable,
BS EN 50214 PVC Insulated Cable,
H05VVH6-F 4 core flat cable
BS EN 50214 H05VVH6-F 4 Core Copper Conductor Flat PVC Insulated Cable
1. AC rated voltage:
Uo: the effective value of voltage between any phase conductor and ground;
U: The effective value of the voltage between any two phase conductors.
2. Operating voltage:
In the AC system, the working voltage is not more than 1.1 times the rated voltage;
In the DC system, the working voltage is not more than 1.5 times the rated voltage.
3. Long-term working temperature of wire core: less than or equal to 65℃.
1. When the insulation resistance of the flat cable is converted to a length of 1km and the temperature is 20℃, the power core should not be less than 30MΩ/km.
2. For the voltage test of the flat cable, the power cores should be able to withstand the 50Hz, 2500V voltage test for 5 minutes, and the control cores should be able to withstand the AC 50Hz, 1500V voltage test.
3. The delivery length of the flat cable should not be less than 150m, and the short-segment cable with a length of not less than 35m should be delivered. The delivery quantity should not exceed 10% of the total delivery length. According to the agreement between the user and the manufacturer, arbitrary The length of the cable is delivered.
|Product name||PVC Insulated Cable|
|Armoured Material||None/Steel Tape/Steel wire|
|Number of cores||1C,2C,3C,4C,5C,3+1C,3+2C,4+1C|
|Section area||1.5MM2 - 400MM2|
PVC Insulated Cable
Contact Person: admin