|Product Name:||PVC Insulated Power Cable||Conductor Material:||Copper|
|Insulation Material:||PVC||Rated Voltage:||0.6/1kV|
|Jacket:||PVC||Number Of Cores:||1-5 Core|
VVR PVC Insulated Power Cable,
Flexible 4 Core Copper Cable VVR,
PVC Insulated Power Cable 0.6/1kV
4 Core Flexible Copper VVR Cable PVC Insulated PVC Sheathed Cable
VVR PVC insulated cable is a copper core PVC insulated and sheathed soft structure power cable with a voltage level of 0.6/1KV. The diameter of each copper wire is about 0.2-0.3mm, and the number of wires is relatively large, so it is relatively soft, suitable for frequently moving power cords, such as computer power cords, etc.
|Product name||PVC Insulated Cable|
|Rated Voltage||0.6/1 KV|
|Armoured Material||None/Steel Tape/Steel wire|
|Number of cores||1C,2C,3C,4C,5C,3+1C,3+2C,4+1C|
|Section area||1.5MM2 - 400MM2|
The difference between RVV and VVR:
1. The name is different.
RVV is generally called a flexible wire, while VVR is called a flexible cable. The full name of RVV is: PVC insulated PVC sheathed flexible cable. The letter R stands for flexible cord. Of course, when R is placed after V, VR stands for PVC soft sheath.
2. The voltage levels are different.
The rated voltage of RVV is 300/500V flexible wire, while the general voltage level of VVR is 0.6/1kV
3. The use occasions are different.
VVR is suitable for frequently moving power cords, such as computer power cords.
4. Different implementation standards.
RVV is manufactured in accordance with the national standard GB/T 5023-2008. VVR manufacturing standards refer to GB/T 12706-2008.
5. The structure is different.
And VVR has the same structure as VV.
6. The number of cable cores is different.
The cross section of RVV conductor is between 0.5-2.5mm2, and the number of cable cores is 2-5. The cross-section of VVR conductor is from 1.5-630mm2, and the number of cable cores is 1-5.
Contact Person: admin