|Product Name:||CU Core Thin Steel Wire Armoured Electrical Cable||Conductor Material:||CU|
|Insulation Material:||PVC||Armour:||Steel Wire|
|Referece Standard:||IEC60502||Package:||Wooden Reel, Iron-wooden Reel, Steel Reel|
1KV Thin Steel Wire Armoured Cable,
PVC Insulated Steel Wire Armoured Cable,
VV32 CU Armoured Cable
CU Core PVC Insulated Thin Steel Wire Armoured Electrical Cable Low Voltage
PVC insulated fine steel wire armored PVC sheathed power cable wire
NYRY armored electrical cable is suitable for transmission and distribution systems with AC rated voltage 0.6/1K and below. It is produced by GB IEC standard, with excellent physical properties and easy to lay and use. Laying in indoor, in mines, in water .
1. Rated voltage: 0.6/1KV
2. Cable core number: single core/multi core
3. The largest. The long-term working temperature of the conductor is 70°C for PVC insulation and 90°C for XLPE insulation.
When short-circuited, the maximum temperature. PVC insulation is 160°C, and XLPE insulation is 250°C.
|Product name||Armoured Electrical Cable|
|Rated Voltage||0.6/1 KV|
|Armoured Material||None/Steel Tape/Steel wire|
|Number of cores||1C,2C,3C,4C,5C,3+1C,3+2C,4+1C|
|Section area||1.5MM² - 400MM²|
During the storage of the cable, the packaging should be standardized to avoid long-term open-air sun exposure, and the two ends should be reliably sealed. Long-term storage in a humid environment is not allowed, and the cable reel cannot be placed flat. The height of the tray should be considered and effectively fixed during transportation. Several trays are not allowed to be hoisted at the same time during hoisting, and it is strictly forbidden to push down from a high place.
Special tools should be used for cable laying, such as pay-off racks, guide rollers, etc., to prevent mechanical damage during the laying process and keep away from heat sources. When laying the cable through the pipe, the inner diameter of the pipe should not be less than 1.5 times the outer diameter of the cable. When multiple cables pass through the pipe, it is forbidden to squeeze the cable. The total area of the cable should not exceed 40% of the total area in the pipe.
Armoured Electrical Cable
Contact Person: admin