|Product Name:||High Voltage Cables||Conductor Material:||Copper|
|Insulation Material:||XLPE||Core:||1, 3,|
|Type:||Medium And High Voltage Cables||Jacket:||PVC|
|Standard:||IEC60502||Rated Voltage:||1-35 Kv|
26/35KV High Voltage Cable N2XY,
26/35KV High Voltage N2XY Cable,
High Voltage Underground Cable N2XY
18/20KV 26/35KV Copper Conductor Medium Voltage Electrical Cables and High Voltage Cables
- Solid or stranded bare copper conductors
- Conforms to DIN VDE 0295 cl.1/cl.2, BS 6360 cl.1/cl.2 and IEC 60228 cl.1/cl.2
- XLPE insulated DIX3 category according to VDE 0276-603/5G
- Color coding according to DIN VDE 0293 (HD 308)
- PVC filling
- PVC outer sheath DMV6 according to HD 603.1
N2XY cross-linked polyethylene insulated cable is mainly a cable used for transmission and distribution of electric energy. It is most commonly used in urban underground power grids, power station introduction lines, internal power supply of industrial and mining enterprises, and underwater cross-river creek transmission lines. Power cables are cable products used for transmission and distribution of high-power electrical energy in the trunk line of power system, including various voltage levels and various insulated power cables of 1-500KV and above.
This product is produced according to GB12706 "rated voltage 35KV copper core, aluminum core plastic insulated power cable" standard, but also according to the user's needs according to the International Electrotechnical Commission recommended standard IEC, British standards, German standards and American standards.
|Product name||XLPE Insulated Cable|
|Armoured Material||None/Steel Tape/Steel wire|
|Number of cores||1C,2C,3C,4C,5C,3+1C,3+2C,4+1C|
|Section area||1.5MM2 - 400MM2|
During storage, the cable should be packed in a standardized manner, avoid long-term open-air exposure, and both ends should be sealed reliably. Long-term storage in a humid environment is not allowed, and the cable tray should not be stored flat. The height of the tray should be considered and fixed effectively during transportation. Multiple pallets are not allowed to be lifted at the same time when lifting, and pushing down from high places is strictly prohibited.
Special tools should be used for cable laying, such as cable release frame, guide roller, etc., to prevent mechanical damage during laying and keep away from heat sources. When laying cables through pipes, the inner diameter of the pipes should not be less than 1.5 times the outer diameter of the cables. When multiple cables pass through the pipeline, it is prohibited to squeeze the cables. The total area of the cable should not exceed 40% of the total area of the pipe.
Medium Voltage Cables
Contact Person: admin